CAN/ULC-S PERIODIC INSPECTIONS AND TEST – DAILY AND MONTHLY. NOTE: Refer to Appendix D for examples of Inspection and Test Record. SCOPE. This Standard provides requirements for the inspection and testing of fire alarm systems and specifies the devices and functions to be inspected. 1 SCOPE This Standard prescribes requirements for the inspection and testing of fire alarm systems and specifies the devices and functions.
|Published (Last):||19 June 2012|
|PDF File Size:||5.16 Mb|
|ePub File Size:||13.75 Mb|
|Price:||Free* [*Free Regsitration Required]|
Test circuit breakers and fuses for proper operation?
Dan communicator has been reset following completion of testing. Pressure regulating control valves shall be inspected. Steam from your hot bath, shower, or operating dishwasher may accidentally “set-off” one of these units. Most fire alarm systems employ zoned annunciators so that fire fighting personnel can be dispatched to the proper area of the building. Interior of dry pipe valve cleaned? Hose hydrostatic test dates are noted on page numbers: Valve supervisory switches tested?
Backflow prevention assemblies shall be inspected locked or properly supervised by an acceptable electrical means.
Correct designations for common control functions and indicators. Nozzle clips in place and nozzles contained?
Date of last compressor service: Ground fault tested on positive and negative initiates trouble signal. P Emergency telephone operable or in-use tone at handset operates. A copy should be maintained on the premises for examination by the Fire Marshal or Inspector at their request.
The fire signal receiving centre transmitter is integral to the fire alarm control unit.
CAN/ULC-S Fire Alarm Annual Inspection Test Form
cab Quick opening devices passed test? The common control employs several features to enable the occupants to identify any specific problems within the system.
Where fault isolation in data communication links is provided between control units or transponders and between transponders, introduce a short circuit fault and confirm annunciation of the fault and operation outside the shorted section between each pair of: Description of the function of each operating control and indicator on the fire alarm control unit.
T Generator provides power to the AC circuit serving the fire alarm system. In-suite signal isolator modules have been identified, individually inspected, and tested.
Seconds Date of trip test from records on site was: Reducer and cap are not missing? Sensitivity tested results are recorded in the Device Test Record. Backflow prevention assembly shall be tested at the design flow.
All sprinkler pressure regulating control valves passed full flow test? It’s a good idea to check the battery compartment every six months for leakage or corrosion on the terminals. Alarm devices inspected to verify they are free from physical damage?
Standards Council of Canada
Status change confirmation inspected and tested. Low points in dry systems drained prior to freezing weather? Documents Flashcards Grammar checker. A B C Confirm that a trouble signal is received at the control unit or transponder under an open loop fault.
Power for ancillary devices is taken from the control unit or transponder that is designed to provide such u,c.
Each power loss i.